The RP-2002 is a six-zone FACP for single and dual hazard
agent releasing applications. The RP-2002 provides reliable
fire detection, signaling and protection for commercial, indus-
trial and institutional buildings requiring agent-based releasing.
The RP-2002 is compatible with System Sensor’s i3 detectors
which are conventional smoke detectors that can transmit a
maintenance trouble signal to the FACP indicating the need for
cleaning and a supervisory ‘freeze’ signal when the ambient
temperature falls below the detector rating of approximately
45°F (7.22°C). In addition, the control panel is compatible with
conventional input devices such as two-wire smoke detectors,
four-wire smoke detectors, pull stations, waterflow devices,
tamper switches and other normally-open contact devices.
Refer to the Notifier Device Compatibility Document for a com-
plete listing of compatible devices.
Four outputs are programmable as NACs (Notification Appli-
ance Circuits) or releasing circuits. Three programmable
Form-C relays (factory programmed for Alarm, Trouble and
Supervisory) and 24 VDC special application resettable and
non-resettable power outputs are also included on the main
circuit board. The RP-2002 supervises all wiring, AC voltage,
battery charger and battery level.
Activation of a compatible smoke detector or any normally-
open fire alarm initiating device will activate audible and visual
signaling devices, illuminate an indicator, display alarm infor-
mation on the panel’s LCD, sound the piezo sounder at the
FACP, activate the FACP alarm relay and operate an optional
module used to notify a remote station or initiate an auxiliary
The RP-2002E offers the same features as the RP-2002 but
allows connection to 220/240 VAC. Unless otherwise speci-
fied, the information in this data sheet applies to both the 110/
120 VAC and 220/240 VAC versions of the panels.